SAE J1488 is the recognized diesel industry filtration standard for diesel: “To determine the ability of a fuel/water separator to separate emulsified or finely dispersed water from fuels. This test method is applicable for biodiesel fuel.” SAE is the Society of Automotive Engineers.
J1488 was updated in 2010 by SAE to account for the reduced interfacial tension (IFT) of ULSD biodiesel blends compared to the higher IFT of pure ULSD.
IFT is the ability of two fluids to repel each other. The high IFT in 100% pure ULSD means that water is easily repelled, and precipitates out to the tank bottom. Water does not bond to ULSD as ULSD is not polar.
Biodiesel is polar, as is water, so water bonds to the biodiesel molecule via a hydrogen bond, hence the lower IFT of biodiesel blends. With this hydrogen bond, the water is more difficult to remove using traditional filters.
There are two phases of the J1488 test procedure; in the first phase 100% pure ULSD, with its high IFT, is used. 2500 ppm emulsified water is added to a dry fuel sample. Since pure ULSD is not polar, the emulsified water is not attracted to, and is not bonded to, the ULSD. Any filter should have as close to 100% efficiency in removing all the water.
In the second phase, the IFT is lowered to 15-19 mN/m, simulating a B20 ULSD biodiesel blend, and again 2500 ppm emulsified water is added. Emulsified water is attracted to, and bonds to, biodiesel, so it is much harder to remove. This is when the hydrogen bonds come into play. In order to reduce the bonded emulsified water to 200 ppm or below, a filters efficiency in breaking the hydrogen bonds to remove water will need to be 92%, (2500 * (1-.92)) = 200.
200 ppm of bonded emulsified water controls the growth of microbes by limiting available water to the microbes; little water, little life, little MIC, corrosion controlled. As well, 200 ppm is the warranty level for emergency backup generators.
A new generation of filters have been developed since 2011 to remove the bonded emulsified water by breaking the hydrogen bonds as tested against SAE J1488. A permanently mounted filtration system is added to the storage tank.
The corrosion control mechanism is supported with field test results. Fuel samples from end users using SAE J1488_201010 filtration consistently show bonded emulsified water levels well below 100 ppm.
Fuel samples that had been taken directly from the return lines, after filtration but before return to the tank, show as little as 10 ppm of bonded emulsified water.
The only time the bonded emulsified water is above 100 ppm is typically after a fuel delivery, which speaks to the quality of fuel delivered, or a water leak into a tank; in that instance the leak was found and fixed. These very low levels of bonded emulsified water content (< 200 ppm) will deny microbes the water needed for growth; little water, little life, little MIC, corrosion controlled.
A key point is that in order to identify the presence of bonded emulsified water, a Karl Fisher titration (ASTM D6304) must be used. Other test methods will not pick up the presence of bonded emulsified water. For example, the visual “clear and bright” test will continue to be “clear and bright” with substantial bonded emulsified water, and no visible free water present.
An additional benefit of SAE J1488 filtration is that if properly installed, and run on an optimal schedule, the sludge and free water that normally deposits on the tank bottom is continually removed, such that storage tanks do not need to be cleaned again. The operational cost of keeping a tank clean is only the electricity used for the filtration system, and annual changeout of filters.